Resin Regeneration Fundamentals - Water Quality Produc
The regeneration of cation and anion exchange resins used in deionizers is a more complicated process than simple softening. The process includes the use of strong acid and caustic. It is important to observe the appropriate safety considerations for handling these …Get a Quote
Boiler Feedwater Demineralizer - Convergence Traini
Ions are atoms or molecules that have split up in water and lost or gained an electron and have thus acquired an electrical charge. Ion exchange is a reversible chemical reaction, in which ions present in a solution are exchanged for a similarly charged ion attached to …Get a Quote
APPLICATION GUIDE Water softening basi
The total time to regenerate is <2 hours and the total water used is about 7 x the resin volume: 15 liter bed = 105 liters (50 gal per ft3). The wastewater is discharged to the sewer or septic system. For a typical home use, a 15 liter (0.53 ft3) softener will serve most needs of a small home.Get a Quote
Ion Exchange Softeners and Dealkalizers – Water Technology .
May 15, 2017· Frequently, a sodium cation softener is combined with a chloride-anion dealkalizer to produce a final product water that is softened and dealkalized. The total dissolved solids have not been reduced by this method, but the softened, dealkalized water is suitable for use as makeup in many boiler feedwater applications.Get a Quote
Water Handbook - Ion Exchange & Water Demineralization | SU
Water flows through a zeolite softener and then an anion unit, which replaces the carbonate, bicarbonate, sulfate, and nitrate ions with chloride ions as shown in these reactions: The chloride anion dealkalizer reduces alkalinity by approximately 90% but does not reduce total solids.Get a Quote
10 ion exchange process - SlideSha
Nov 19, 2015· 10 ion exchange process 1. Ion Exchange Process 2. Ions • Electrically charged atoms or molecules (Cations and Anions) – can have one or more charges (mostly 1 to 3), and can be made of one or more atoms – Mono-atomic ions: Mono-valent ions (Na+ and Cl-), divalent ions (Ca+2), trivalent ions (Al+3) – Polyatomic ions: Mono-valent ions (NH4 +1 and NO3 -1), Di-valent ions (CO3 -2, and ...Get a Quote
Type II Anion vs Type I Anion: Ion Exchange Resin Analysis .
Aug 07, 2008· While the heated water is beneficial for boiler feedwater, it is not good for regeneration of the anion resins. This water can approach and possibly exceed 130 degrees F. The Type II strong base anion resin temperature limit is stated by manufacturers at 105 degrees F, however, it is more prudent to maintain the limit to a maximum of 95 degrees F.Get a Quote
Ion exchange in the brewing and beverage industry - EU
A strongly acidic cation exchanger exchanges all ca tions present in water against H + ions during regeneration with HCl and H 2 SO 4 or against Na + ions in the regeneration with NaCl. In the latter case the exchanger is called softener and is applied for instance for the treatment of service water or boiler feed water.Get a Quote
Performance Expectation of Ion ... - Water Tech Onli
The water source is a medium sized river with an ionic loading averaging 83 ppm TDS, a Total Na/Total Cation of 18%, Total SiO 2 /Total Anion of 4%, and a TOC of .20 ppm. Since individual demineralizers will perform differently from location to location, the comparison of both the system and resin performance is based on the water quality in ...Get a Quote
Cation-Anion | PCA Wat
The advantage of a cation-anion exchanger is that it provides a very good quality of demineralised water. In addition, relatively little waste water is released. The disadvantage is that the system cannot produce demineralised water during regeneration. Such a regeneration takes several hours, depending on the resin volume.Get a Quote
Res-Kem Blog: Type II Anion vs Type I Anion: Ion Exchange .
While the heated water is beneficial for boiler feedwater, it is not good for regeneration of the anion resins. This water can approach and possibly exceed 130 degrees F. The Type II strong base anion resin temperature limit is stated by manufacturers at 105 degrees F, however, it is more prudent to maintain the limit to a maximum of 95 degrees F.Get a Quote
Boiler Water Treatment untuk Pencegahan Masalah - Artikel .
Boiler water treatment adalah bagian dari program perawatan boiler dengan boiler chemical yang diaplikasikan di fasa air. Adapun jenis chemical yang dipakai dalam water treatement tersebut meliputi chemicals untuk penjernihan air, penghambat kerak, penghambat korosi, kontrol pH dan untuk …Get a Quote
How to Calculate Resin Capacity for Softener - Water Chemist
Quantity of water to be treated = 25000 liter/ hour Ion exchange capacity of resin to be used in the plant = 10 kg of hardness / cub.m Salt required for regeneration of resin= 45 kg/ cub.m of the resin The water softening plant works 2 shifts of 8 hours per day. Assume any suitable data where necessary. thank uGet a Quote
Ion Exchange / DM plant calculations, page
Dec 26, 2013· A discussion started in 2004 but continuing through 2018. December 26, 2013. Q. Good Evening Sir, In our softening plant we regenerate resin with 16% Sodium Chloride, same as how much qty of Sodium Hydroxide, Hydrochloric acid want to regenerate for Cation and anion resin.Get a Quote
Choosing the Right Dealkalizer for Your System | AquaAnalyti
Sep 21, 2019· A dealkalizer is a pre-treatment device commonly seen in boiler rooms which is responsible for removing carbonate alkalinity in the feed water before it reaches the boiler. To formulate a proper pre-treatment solution for your system, a thorough understanding of incoming water …Get a Quote
Ion Exchange for Dummies - Water Treatment and Purificati
water. Ions are able to move around in water, they are not fixed, and they are not attached to ions of the opposite charge. Only to sum of the charges is the same for all cations and all anions. See figure 1 for a schematic representation of ions in water. Lenntech firstname.lastname@example.org Tel. +31-152-610-900 www.lenntech.com Fax. +31-152-616-289Get a Quote
Online Available at www.chemijournal.com International .
regeneration, once exhausted. The exhausted cation resin, in hydrogen form, is regenerated by hydrochloric acid (HCl) and the anion resin by sodium hydroxide solution. Depending on the water quality, ion exchange resins may get fouled in different ways, resulting in loss of resin efficiency to deliver pure water.Get a Quote
Comparing Water Treatment Options for Boiler Operations .
Aug 24, 2020· This is an ion exchange method of treating water with cation and anion resins, either by vessels arranged in series or (in the case of mixed bed) with a single vessel containing both resins. These resins must be regenerated as the cations and anions (respectively) are consumed. Disadvantages: Hazardous chemicals required for regeneration of the ...Get a Quote
Anion Removal, Demin Process – Flow meters Indones
Mar 17, 2017· The exchangeable anion is OH-, which is picked up by the strong base anion resin during regeneration with caustic (NaOH). The cation in the water passing through unmodified (hydrogen ion is the cation) combines with the OH- liberated during the exchange and leaves the anion unit as molecules of water …Get a Quote
(PDF) Utilization of Ion-Exchange Technology for Boiler .
A final resin volume of around 2.2 litres was selected. ... demineralizer units consisting of cation and anion exchange units, ... developed for the removal of dissolved oxygen from boiler feed ...Get a Quote
Culligan Exchange Tank Deionization Servi
Water qualities of 15 megohm or more, with a neutral pH, can typically be attained. CATION S-ANION MIXED BED High Purity Water Systems From A Single Tank To A Complete System. Culligan high purity water systems using exchange tanks are available in several system configurations. Your Culligan dealer selects the sizes,Get a Quote